Q: will this item work on a electric Combi boiler.
A: As long as the boiler accepts normal on/off heating controls. The boiler manufacturer will confirm.
Q: at this time i have 1 transmitter with 1 reciever,can i put another reciever for example upstairs with using just the one transmitter.
A: I'm afraid not.
Q: What is the FROST PROTECT SETTING...meaning what does that do/its purpose? what number setting should it be at in the winter?
A: It is protect your house from frost (burst pipes). I would recommend 5C.
Q: Can the Delta Dore Tybox137 be set to display the room temperature as well as/rather than the temperature that the controller is aiming at?
A: You can change the temperature displayed by changing option 2-04 in the installers menu (see installation instructions).
During auto mode you can press the i button to see the other temperature.
Q: How do I connect to my boiler I just moved in ??
A: If it is a combi boiler, it just wires to the thermostat terminals as well as the live and neutral terminals.
Q: My living room has 3 electric radiators. Can I purchase additional receivers to work with the Tybox 137? If so at what cost?
A: The included receiver is not suitable for electric radiators. So you would have to buy the transmitter and receivers separately, please email us at firstname.lastname@example.org with how many receivers you require and we will get a price for you.
Q: Dear Srs,
Is this thermostat compatible with Ariston Egis Plus 24 FF?
A: Yes it is.
Q: What radio frequency is using Tybox 137. We have problems with internet router situated close to Tybox transmitter. The heating stop working due to some interferences between both.
A: It is 868Mhz. It should be at least 1.5m away from other wireless devices.
Q: Hi. Is the Tybox 137 compatible with the WB Greenstar 30i ErP condensing boiler? My father-in-law currently has the Salus ST630 with RF boiler control which he just can`t get the hang of using.
A: Yes it is.
Q: How does the control update once it has been serviced to get rid of the spanner? Thanks
A: Turn the dial to the power position.
Press the I button for 5 seconds
Press the 2 button to enter the installer menu
Press OK several times to get to menu 2-07
Use the + button to change it to 365 days (or amount of days until the next service)
Turn the dial to auto to exit the installer menu and return to programme
Q: how do i overide the programme during the period when it is switched off
A: You can press the top button to override it to comfort mode.
Q: Is this control compatible with a biasi activa 25c combi boiler?
A: Yes it is.
Q: Dear Sir/Madam, I wonder if TyBOX 137 is compatible with TYBOX 23. I would like to change transmitter 23 for 137 without changing already installed receiver. Please let me know. Thank you very much. Best regards, Marcela Stankusova
A: Yes you can.